06-03-2013 08:46 AM
A couple weeks ago we had a power down at our data center. When power was restored and we brought the SAN infrastructure up we experienced zero issues. However, when I looked at our SAN Directors via Network Advisor they both have a Red diamond for the switches as though there's a problem. I also ran a Healthcheck against both switches and the healthcheck shows them as having a status of DOWN.
Anybody know what's going on or what I can do to get rid of the red diamonds?
06-03-2013 09:07 AM
psshow shows the following for both switches...............
Power Supply #1 is OK
V10H30, AGC2M30HEG2 ,23-0000067-01, B,DELTA,ECD14020006 ,06,AGC2M30H
Power Supply #2 is absent
Power Supply #3 is faulty
0HEGC ,23-0000067-01, B,DELTA,ECD14020006 ,06,AGC2M30HE
Power Supply #4 is absent
06-03-2013 10:42 AM
All is well now. Apparently during the power outage the power supply to the directors was changed and the circuits were not activated which caused PS3 to be down/faulty.
Thanks a lot for your quick reply and assistance.